|Tightening torque||5.31 lbf.in (0.6 N.m) (with flat Ã˜ 3.5 mm)|
|Connections - terminals||Screw type terminals 1 0.14 - 2.5 mmÂ² 26...14 flexible without cable end|
|Screw type terminals 1 0.09 - 1.5 mmÂ² 28...16 flexible with cable end|
|Screw type terminals 1 0.14 - 2.5 mmÂ² 26...12 solid|
|Screw type terminals 2 0.09 - 0.75 mmÂ² 28...20 flexible with cable end|
|Screw type terminals 2 0.2 - 2.5 mmÂ² 24...14 solid|
|[Ui] rated insulation voltage||2000 V terminals/mounting rails|
|300 V IEC 60947-1 coil circuit/contact circuits|
|[Uimp] rated impulse withstand voltage||2.5 kV|
|[Us] rated supply voltage||19...30 V IEC 61131-2|
|Current per output common||<=16 A|
|Short circuit protection||1 A internal fuse 5 x 20 mm fast blow PLC end|
|2 A fuse per channel 5 x 20 mm fast blow output circuit|
|Supply circuit type||DC|
|Supply current||<=1 A|
|Voltage drop on power supply fuse||0.3 V|
|Status LED||1 LED per channel green channel status|
|1 LED green power ON|
|Fixing mode||By clips 35 mm symmetrical DIN rail|
|By screws solid plate with fixing kit|
|Installation category||II IEC 60664-1|
|Tightening torque||0.6 N.m flat Ã˜ 3.5 mm|
|Number of channels||16|
|Product or component type||Sub-base for plug-in relay|
|Range of product||Advantys Telefast ABE7|
|Sub-base type||Output sub-base|
|Common description||BASE FOR EM/SS RELS FUSE WITHOUT COM.-|
MRO Electric repairs CNCs, PLCs, Servo/Spindle Drives, Motors, Amplifiers, VFDs, HMIs, and more, most of which can be repaired in only 3-5 days.
MRO can restore your failed ABE7P16T334 to remanufactured condition and save you up to 75% compared to buying new. We offer standard repair pricing to ensure you the best value for your repair.
Our certified technicians use rigorous testing procedures to ensure your parts are restored to fully functioning condition. Our team proudly stands behind all repairs by providing a minimum 2 year warranty.
Our technicians have vast experience with most manufacturers and models. In addition to this ABE7P16T334 we also repair drives, motors, PLCs and more, so if you don’t see the model you need, please contact us.
If you are interested in getting credit for your faulty ABE7P16T334, just let us know and we can issue you an RMA to send it in as an exchange. Our exchange program provides you with savings and keeps us stocked for the next time you need anything.
Want it shipped tomorrow?
Ask about exchanging your faulty ABE7P16T334 for credit when ordering from MRO Electric
The ABE7P16T334 is a Sub-Base For PLug-In Relay Abe7 - 16 Channels - F... that is manufactured by Schneider Electric. These products are manufactured in France and are designed for Material handling, packaging, and textile machines usage. All of the products in the modicon-communication line come with a 2 year warranty from MRO Electric. We also carry Telefast from other manufacturers such as Modicon and ABB.
Check out the rest of our Schneider Electric product line. Whether it's using our online instant quote feature, giving us a call at (800) 691-8511, or sending us an email at firstname.lastname@example.org, we strive for customer satisfaction first. This means lower prices and better service for you. For more products like ABE7P16T334, take a look at more from our Robotics line. If your current unit has gone bad, take advantage of our Core Exchange program for the most inexpensive route. You can learn more about this program on our FAQ page here. We offer a repair service on all of our ABE7P16T334 products that keep your downtime to a minimum. To stay up to date on manufacturer news, as well as access any of our datasheets, manuals, or other documentation, we suggest you take a look at our blog.
Over 1600 Ratings from Actual CustomersRead Our Reviews
thanks for your attenion and follow up. very good customer service is hard to come by right now. i appreciate the servic...dan
You were awesome - I appreciate your great customer service and helpful attitude! Thank you for making the ordering proc...Arun
MROelectric always comes through for us. Their speed is phenomenal, I don't know how much more you could ask from a comp...Sherman