|Range of product||Altivar 61|
|8.2 A for 380 V 3 phases 2.2 kW / 3 hp|
|12...16 kHz with derating factor|
|Flux vector control without sensor, standard|
|Voltage/frequency ratio, 5 points|
|Voltage/frequency ratio - Energy Saving, quadratic U/f|
|Communication card for BACnet|
|Communication card for CC-Link|
|Controller inside programmable card|
|Communication card for DeviceNet|
|Communication card for EtherNet/IP|
|Communication card for Fipio|
|I/O extension card|
|Communication card for Interbus-S|
|Communication card for LonWorks|
|Communication card for METASYS N2|
|Communication card for Modbus Plus|
|Communication card for Modbus TCP|
|Communication card for Modbus/Uni-Telway|
|Communication card for Profibus DP|
|Communication card for Profibus DP V1|
|Product or component type||Variable speed drive|
|Product specific application||Pumping and ventilation machine|
|Motor power kW||2.2 kW, 3 phases at 380...480 V|
|Motor power hp||3 hp, 3 phases at 380...480 V|
|Power supply voltage||380...480 V - 15...10 %|
|Supply number of phases||3 phases|
|Line current||7.1 A for 480 V 3 phases 2.2 kW / 3 hp|
|EMC filter||Level 3 EMC filter|
|Assembly style||With heat sink|
|Apparent power||5.4 kVA at 380 V 3 phases 2.2 kW / 3 hp|
|Maximum prospective line Isc||5 kA for 3 phases|
|Maximum transient current||6.9 A for 60 s, 3 phases|
|Nominal switching frequency||12 kHz|
|Switching frequency||1...16 kHz adjustable|
|Asynchronous motor control||Voltage/frequency ratio, 2 points|
|Synchronous motor control profile||Vector control without sensor, standard|
|Communication port protocol||Modbus|
|Type of polarization||No impedance for Modbus|
|Option card||Communication card for APOGEE FLN|
MRO Electric repairs CNCs, PLCs, Servo/Spindle Drives, Motors, Amplifiers, VFDs, HMIs, and more, most of which can be repaired in only 3-5 days.
MRO can restore your failed ATV61HU22N4 to remanufactured condition and save you up to 75% compared to buying new. We offer standard repair pricing to ensure you the best value for your repair.
Our certified technicians use rigorous testing procedures to ensure your parts are restored to fully functioning condition. Our team proudly stands behind all repairs by providing a minimum 2 year warranty.
Our technicians have vast experience with most manufacturers and models. In addition to this ATV61HU22N4 we also repair drives, motors, PLCs and more, so if you don’t see the model you need, please contact us.
If you are interested in getting credit for your faulty ATV61HU22N4, just let us know and we can issue you an RMA to send it in as an exchange. Our exchange program provides you with savings and keeps us stocked for the next time you need anything.
Want it shipped today?
Ask about exchanging your faulty ATV61HU22N4 for credit when ordering from MRO Electric
The ATV61HU22N4 is a 3-Phase 2.2 kW 460 Volt AC Drive that is manufactured by Schneider Electric. These products are manufactured in France and are designed for Material handling, packaging, and textile machines usage. All of the products come with a 2 year warranty from MRO Electric. We also carry AC Drives from other manufacturers such as Modicon and ABB.
Check out the rest of our Schneider Electric product line. Whether it's using our online instant quote feature, giving us a call at (800) 691-8511, or sending us an email at firstname.lastname@example.org, we strive for customer satisfaction first. This means lower prices and better service for you. For more products like ATV61HU22N4, take a look at more from our AC Drives line. If your current unit has gone bad, take advantage of our Core Exchange program for the most inexpensive route. You can learn more about this program on our FAQ page here. We offer a repair service on all of our ATV61HU22N4 products that keep your downtime to a minimum. To stay up to date on manufacturer news, as well as access any of our datasheets, manuals, or other documentation, we suggest you take a look at our blog.
Over 1650 Ratings from Actual CustomersRead Our Reviews
Shipped quickly! Easy to use website. Very impressed with your company!Frank
I appreciate all the help you and Adam provided. Sales and customer service team provided excellent support. You all hav...PMSI
Panel was received this morning and we are up and running. Thank you for your assistance getting it out to us earlier th...jeff