|Type of filter||Notch filter - 3 dB at 50/60 Hz|
|Single pole low pass - 3 dB at 20 Hz|
|Analogue input number||8|
|Addressing requirement||10 input words|
|Analogue input type||Thermocouple - 210...760 Â°C thermocouple J|
|Thermocouple - 270...1000 Â°C thermocouple E|
|Thermocouple - 270...1370 Â°C thermocouple K|
|Thermocouple - 270...400 Â°C thermocouple T|
|Thermocouple - 50...1665 Â°C thermocouple R|
|Thermocouple - 50...1665 Â°C thermocouple S|
|Analogue input resolution||16 bits|
|Input impedance||> 1 MOhm|
|Absolute accuracy error||+/- 2 Â°C plus + 0.1 % of reading thermocouple J|
|+/- 2 Â°C plus + 0.1 % of reading thermocouple K|
|+/- 2 Â°C plus + 0.1 % of reading thermocouple T|
|+/- 4 Â°C plus + 0.1 % of reading thermocouple R|
|+/- 4 Â°C plus + 0.1 % of reading thermocouple S|
|+/- 2 Â°C plus + 0.1 % of reading thermocouple E|
|Linearity error||1 Â°C, 0.1 Â°C, 1 F, 0.1 F - 210...760 Â°C|
|1 Â°C, 0.1 Â°C, 1 F, 0.1 F - 270...1000 Â°C|
|1 Â°C, 0.1 Â°C, 1 F, 0.1 F - 270...1370 Â°C|
|1 Â°C, 0.1 Â°C, 1 F, 0.1 F - 270...400 Â°C|
|1 Â°C, 0.1 Â°C, 1 F, 0.1 F - 50...1665 Â°C|
|Accuracy drift according to||0.15 ÂµV/Â°C + 0.0015 % of reading/Â°C max low level voltage|
|Common mode rejection||>= 120 dB 50/60 Hz|
|Isolation between channels and bus||1780 V AC for 60 s|
|2500 V DC for 60 s|
|Isolation between channels||300 V DC|
|220 V AC|
|Update time||1000 ms|
|Fault type||Broken wire|
|Cold junction compensation||Internal 0...60 Â°C|
|Local signalling||1 LED green bus communication is present (Active)|
|1 LED red external fault|
|8 LEDs green channel is turned on|
|8 LEDs red channel fault|
|Bus current requirement||280 mA|
|Power dissipation in W||1.5 W|
This product weights 1lb. Want it shipped today?
What is the product warranty?
Showing 5 out of over 1,150 reviews. See All
Everyone I have talked with at MRO Electric was knowledgeable, helpful and courteous. The modules I purchased are no longer in production so finding a source for them allows me to delay the large expense of replacing the entire fountain controller for a bit longer. I recommend MRO Electric without hesitation.
Joe Kaminski was great helping with the PLC but also as a go between with us and the programming company as well. Joe was very good on the customer service side of the business as well which many companies don't have anymore. Highly recommend MRO Electric to do business with. Thanks
Like the Service that was provided by JK, Great customer service. Happy to know sonmeone still service Modicon PLC units. Fast and efficient.
We are very happy with the service that MRO provided to us. They had stock of an older PLC that we couldn't find anywhere and were able to have it ready for a courier to pick it up so we had our machine back up the same day. MRO will be the first place we check going forward.
MRO was able to ship us a refurbished Modicon PLC with a great warranty option at a price that no one else could match. I highly recommend this company!