|Product weight||0.085 kg|
|Range of product||Modicon M238 logic controller|
|Product or component type||Analog input module|
|Analogue input number||4|
|Analogue input type||Current 4...20 mA non differential|
|Voltage 0...10 V non differential|
|Temperature probe - 200...600 Â°C Pt 100/Pt 1000 non differential|
|Temperature probe - 50...150 Â°C Ni 100/Ni 1000 non differential|
|Cross talk||<= 1 LSB|
|Range compatibility||Advantys OTB|
|Analogue input resolution||12 bits|
|LSB value||0.2 Â°C temperature probe Pt 100/Pt 1000|
|0.05 Â°C temperature probe Ni 100/Ni 1000|
|2.5 mV voltage voltage|
|4.8 ÂµA current current|
|Permissible continuous overload||13 V voltage|
|40 mA current|
|Input impedance||>= 10 kOhm temperature probe|
|10 kOhm voltage|
|470 Ohm current|
|Sampling duration||<= 160 ms|
|Acquisition period||160 ms per channel + 1 controller cycle time voltage/current|
|320 ms per channel + 1 controller cycle time temperature probe|
|Measurement error||+/- 0.4 % of full scale Pt 100/Pt 1000, Ni 100/ Ni 1000 25 Â°C|
|+/- 0.2 % of full scale 0...10 V 0...10 V 25 Â°C|
|+/- 0.2 % of full scale 4...20 mA 4...20 mA 25 Â°C|
|Temperature coefficient||+/- 0.004 %FS/Â°C temperature probe|
|+/- 0.009 %FS/Â°C current|
|+/- 0.009 %FS/Â°C voltage|
|Repeat accuracy||+/-0.1 %FS|
|Non-linearity||+/- 0.02 %FS|
|Total error||+/-0.5 %FS|
|Type of cable||Shielded cable|
|Insulation between channel and||Photocoupler|
|[Us] rated supply voltage||24 V DC|
|Supply voltage limits||20.4...28.8 V|
|Electrical connection||1 removable screw terminal block|
|Current consumption||50 mA 5 V DC internal|
|60 mA 24 V DC external|
This product weights 1lb. Want it shipped today?
What is the product warranty?
Showing 5 out of over 1,200 reviews. See All
Everyone I have talked with at MRO Electric was knowledgeable, helpful and courteous. The modules I purchased are no longer in production so finding a source for them allows me to delay the large expense of replacing the entire fountain controller for a bit longer. I recommend MRO Electric without hesitation.
Joe Kaminski was great helping with the PLC but also as a go between with us and the programming company as well. Joe was very good on the customer service side of the business as well which many companies don't have anymore. Highly recommend MRO Electric to do business with. Thanks
Like the Service that was provided by JK, Great customer service. Happy to know sonmeone still service Modicon PLC units. Fast and efficient.
We are very happy with the service that MRO provided to us. They had stock of an older PLC that we couldn't find anywhere and were able to have it ready for a courier to pick it up so we had our machine back up the same day. MRO will be the first place we check going forward.
MRO was able to ship us a refurbished Modicon PLC with a great warranty option at a price that no one else could match. I highly recommend this company!