|Product or component type||Dc discrete output module|
|Discrete output number||32|
|Group of channels||4 groups of 8|
|Discrete output logic||Negative logic (sink)|
|Addressing requirement||2 output words|
|Discrete output voltage||24 V DC|
|Output voltage limits||19.2...30 V|
|Absolute maximum output||56 V for 1.3 s decaying pulse|
|Voltage drop||0.4 V 0.5 A|
|Maximum load current||4 A per group|
|16 A per module|
|Surge current||<= 5 A for 0.0005 s|
|Response time||<= 1 ms at state 1 to state 0|
|<= 1 ms at state 0 to state 1|
|Leakage current||0.4 mA 30 V|
|Load inductance||Inductance(H) = 0.5/((current(A))Â² x (switching frequency(Hz))) 50 Hz|
|Fault indication||Blown fuse|
|Loss of field power|
|Associated fuse rating||5 A per group|
|3 A each point|
|Isolation between channels and bus||1780 Vrms DC for 1 minute|
|Isolation between group||500 Vrms DC for 1 minute|
|Protection type||Internal output protection by 5 A fuse per group|
|Power dissipation||1.75 W + (0.4 V x total module load current)|
|Local signalling||32 LEDs green input status|
|1 LED red external fault detected (F)|
|1 LED green bus communication is present (Active)|
|Bus current requirement||330 mA|
This product weights 3lbs. Want it shipped today?
What is the product warranty?
Showing 5 out of over 1,150 reviews. See All
Everyone I have talked with at MRO Electric was knowledgeable, helpful and courteous. The modules I purchased are no longer in production so finding a source for them allows me to delay the large expense of replacing the entire fountain controller for a bit longer. I recommend MRO Electric without hesitation.
Joe Kaminski was great helping with the PLC but also as a go between with us and the programming company as well. Joe was very good on the customer service side of the business as well which many companies don't have anymore. Highly recommend MRO Electric to do business with. Thanks
Like the Service that was provided by JK, Great customer service. Happy to know sonmeone still service Modicon PLC units. Fast and efficient.
We are very happy with the service that MRO provided to us. They had stock of an older PLC that we couldn't find anywhere and were able to have it ready for a courier to pick it up so we had our machine back up the same day. MRO will be the first place we check going forward.
MRO was able to ship us a refurbished Modicon PLC with a great warranty option at a price that no one else could match. I highly recommend this company!