MANUFACTURER: Schneider Electric
DESCRIPTION: Distributed Analog Output - 4 Output - 4..20 Ma
PRODUCT TYPE INFO: Modicon Momentum
|Width||5.57 in (141.5 mm)|
|Range of product||Modicon Momentum automation platform|
|Product or component type||Analogue output base|
|Analogue output number||4|
|Data format||Full 16 bits signed|
|Analogue output range||+/- 10 V 12 bits + sign >= 1 kOhm|
|4...20 mA 12 bits + sign <= 0.6 kOhm|
|Load capacitance||< 1 ÂµF|
|Absolute accuracy error||+/- 0.2 % of full scale +/- 10 V 77 Â°F (25 Â°C)|
|+/- 0.25 % full scale +/- 10 V 140 Â°F (60 Â°C)|
|+/- 0.4 % of full scale 4...20 mA 77 Â°F (25 Â°C)|
|+/- 0.5 % of full scale 4...20 mA 140 Â°F (60 Â°C)|
|Temperature drift||10 %oFS/Â°C +/- 10 V 140 Â°F (60 Â°C)|
|30 %oFS/Â°C 4...20 mA 140 Â°F (60 Â°C)|
|Update time||< 2 ms|
|Full scale||10 V +/- 10 V|
|2 mA 4...20 mA|
|Fail state||Reset to full scale|
|Reset to zero|
|Isolation between channels and ground||500 V AC for 1 minute|
|Power dissipation in W||<= 8.5 W|
|Protection type||Internal 2 A slow-blow|
|Output short-circuit protection||With in voltage circuit|
|External power requirement||+/- 30 V DC|
|24 V DC|
|Permissible common mode voltage||250 V 47...63 Hz AC between channels to ground|
|250 V 47...63 Hz DC|
|Reverse polarity protection||Internal|
|Local signalling||4 LEDs channel status|
|Current consumption||150 mA 24 V DC actuator|
|530 mA 24 V DC base|
|Height||4.92 in (125 mm)|
|Depth||1.87 in (47.5 mm)|
MRO Electric repairs CNCs, PLCs, Servo/Spindle Drives, Motors, Amplifiers, VFDs, HMIs, and more, most of which can be repaired in only 3-5 days.
MRO can restore your failed 170AAO92100 to remanufactured condition and save you up to 75% compared to buying new. We offer standard repair pricing to ensure you the best value for your repair.
Our certified technicians use rigorous testing procedures to ensure your parts are restored to fully functioning condition. Our team proudly stands behind all repairs by providing a minimum 2 year warranty.
Our technicians have vast experience with most manufacturers and models. In addition to this 170AAO92100 we also repair drives, motors, PLCs and more, so if you don’t see the model you need, please contact us.
If you are interested in getting credit for your faulty 170AAO92100, just let us know and we can issue you an RMA to send it in as an exchange. Our exchange program provides you with savings and keeps us stocked for the next time you need anything.
Want it shipped today?
Ask about exchanging your faulty 170AAO92100 for credit when ordering from MRO Electric
The 170AAO92100 is a Distributed Analog Output - 4 Output - 4..20 Ma that is manufactured by Schneider Electric. These products are manufactured in France and are designed for Material handling, packaging, and textile machines usage. All of the products come with a 2 year warranty from MRO Electric. We also carry I/O Modules from other manufacturers such as Modicon and ABB.
Check out the rest of our Schneider Electric product line. Whether it's using our online instant quote feature, giving us a call at (800) 691-8511, or sending us an email at firstname.lastname@example.org, we strive for customer satisfaction first. This means lower prices and better service for you. For more products like 170AAO92100, take a look at more from our I/O Modules line. If your current unit has gone bad, take advantage of our Core Exchange program for the most inexpensive route. You can learn more about this program on our FAQ page here. We offer a repair service on all of our 170AAO92100 products that keep your downtime to a minimum. To stay up to date on manufacturer news, as well as access any of our datasheets, manuals, or other documentation, we suggest you take a look at our blog.
Over 1650 Ratings from Actual CustomersRead Our Reviews
Shipped quickly! Easy to use website. Very impressed with your company!Frank
I appreciate all the help you and Adam provided. Sales and customer service team provided excellent support. You all hav...PMSI
Panel was received this morning and we are up and running. Thank you for your assistance getting it out to us earlier th...jeff